Without enough D.O. concentration, the beneficial microorganisms will die while troublesome filamentous microbes proliferate, causing some sludge settling problems. If the D.O. content becomes too high, energy is then wasted, and the expensive aeration equipment endures a great deal of unneeded wear.
Recently, a small mid-Western city decided to investigate ways to improve the efficiency of their waste treatment plant. The facility operator was interested in pursuing further aeration system improvements at the plant. He had learned from an operator of a nearby treatment plant that their use of a continuous measurement system for monitoring process D.O. helped them respond to rapid increases in plant load. The operator wanted to apply this strategy to achieve automatic control of blower speed and further reduce energy costs.
The city consulting engineer and plant operator joined forces to complete a simple study that evaluated the cost effectiveness of process D.O. measurement and automatic aeration control. Over the course of a five-month period, the following data was collected:
- D.O. concentration in the contact tank
- D.O. concentration in the re-aeration tank
- Time of day that D.O. measurement was made
- Energy consumption (in kWh) for the preceding day
- Percent speed at which the variable frequency drive (VFD) had been operating during the preceding day.
Analysis of the data disclosed that each 10% reduction of blower speed decreased the daily energy use by about 40 kWh. These results confirmed that using an automatic controller to regulate blower speed would significantly reduce energy use. Subsequently, the plant operator installed an automatic D.O. monitoring /control system for a six-month trial. A control set point of 2 mg/l D.O. concentration was established for the trial.
During part of this trial a single blower was used. When two blowers were used, they were operated simultaneously under the control of the automatic system. Both VFDs were set to operate at a minimum speed of 50%. Over the course of this trial period, total plant energy consumption was reduced by about 8%.
The U.S. Environmental Protection Agency Design Manual on Fine Pore Aeration Systems (EPA/625/1-89-023) states: "energy saving achievable by automatic aeration on D.O. control is 25% to 40%, but can be as high as 50%." Realistically, a waste treatment plant can expect energy savings of anywhere from 0% up to 50%. Many factors influence the magnitude of energy savings, including plant size, mixing limitations, type of aeration equipment used, and plant loading. It is recommended to conduct a feasibility study to determine the potential cost savings.
For further information, call GLI International at 414-355-3601.