Managing Nutrient Pollution
In its July 2007 report, “Effects of Nutrient Enrichment in the Nation’s Estuaries: A Decade of Change, National Estuarine Eutrophication Assessment Update,” the National Oceanic & Atmospheric Administration (NOAA) said that nutrient pollution is getting worse in many estuaries throughout the U.S., especially those on the heavily populated East Coast.
Nutrients such as phosphorus and nitrogen trigger algae blooms and reduce the amount of life-giving oxygen in the water. The report said the increased nutrient loading is linked to human activities upstream from the estuaries.
Nevertheless, the NOAA report noted that some of the nation’s estuaries have shown significant improvement in reducing nutrient pollution. One of those waterways, the Tampa Bay, Fla., Estuary, has long implemented a program of aggressive nutrient management that has reversed the trend of increased nutrient pollution. Since 1978, the estuary has benefited from the use of a denitrification system that reduces nitrate-nitrogen (NO3-N) and suspended solids (SS) to meet stringent government standards at the Howard F. Curren Advanced Waste-water Treatment Plant—the world’s largest denitrification plant.
The plant utilizes a TETRA Denite denitrification system from Severn Trent Services. It was first installed in 1988 and expanded in 1992. The fixed-film biological denitrification process removes NO3-N and SS in a single treatment step. The system can also be integrated with other plant treatment processes to provide superior total nitrogen (TN) and total phosphorus (TP) removal. Denite is used as the final treatment step in a TN removal process to help a facility meet stringent TN discharge limits of less than 3 mg/L.
The improvement in filtered effluent quality of the large flow from this plant has been a documented factor in the revitalization of Tampa Bay over the last few decades. Sea grasses and sport fish have returned to once barren areas of the waterway.
Ten years of effluent data (1997 to 2006) reveal the following results: average flow of 55.43 million gal per day; biological oxygen demand (BOD) of 2.52 mg/L; TN of 2.46 mg/L; and total suspended solids (TSS) of 0.93 mg/L.
The Denitrification Process
The Howard F. Curren Plant, the only wastewater treatment plant in the Tampa area, receives waste from the city of Tampa and parts of Hillsborough County. Incoming wastewater contains approximately 200 ppm BOD, 200 ppm SS and 40 to 45 ppm total Kjeldahl nitrogen (TKN).
Effluent standards are 5 mg/L or ppm BOD, 5 ppm TSS and 3 ppm TN. The plant has received a variance on TP, as eastern Tampa Bay is the largest U.S. depository of “bone rock,” which is used for fertilizer production and is the cause of background TP in the bay.
The plant’s first treatment step is odor control, which is accomplished with an odor control spray tower that uses caustic soda to reduce sulfur dioxide. Screen and grit removal is then performed in two side-by-side buildings. The sugar sand prevalent in Florida’s raw wastewater is removed in concrete tanks, where sand and grit slurrie is pumped to Dorr Oliver cyclone separators and grit washers, then to trucks that take the grit to a landfill. These buildings also contain Hycor stainless steel, self-cleaning screens with approximately 2-mm gaps to remove larger particles.
The wastewater then goes to rectangular primary clarifiers to achieve approximately 30% BOD removal and 60% SS removal. The sludge from the primary clarifiers flows to anaerobic digesters, where the methane gas is recovered to power the plant’s generators.
Wastewater is pumped to the high-purity oxygen basins where oxygen from two cryogenic plants (an 80- and a 60-ton-per-day) is injected into the annulus of covered basins and 24 slow-speed mixers continue the BOD removal process.
Next, the wastewater flows to another set of rectangular intermediate clarifiers, and secondary sludge from the carb final tanks is thickened and pumped into the anaerobic digesters with the settled primary sludge. Digested sludge is then dewatered on 2-meter belt presses and heat-dried or land-applied. The resulting filter cake is elevated to a gas-fired kiln, where the biosolids are turned into pellets, stored and eventually sold for fertilizers.
After exiting the intermediate clarifiers, the wastewater flows to nitrification basins where compressed air is introduced at the basin bottoms through fine-bubble Sanitaire diffusers. The nitrification process is completed when the ammonia nitrogen is converted to soluble nitrate-nitrogen. After final clarification in rectangular clarifiers, methanol is added to the wastewater stream as it enters the Denite filters. Nitrate-nitrogen levels are often in the 20- to 30-ppm range, as belt press filtrate also is combined with the filter feed.
Filtrate is returned from the high-purity oxygen reactors to carbon final tanks, nitrification diffused-air reactors to be nitrified (press filtrate has 500 to 1,000 mg/L ammonia nitrogen). The Denite filters remove TSS and NO3-N in one step.
Filtered effluent then flows to re-aeration and disinfection basins, where chlorine is introduced. Sulfur dioxide is added to dechlorinate the wastewater after it goes over the weir, but before it is piped less than one mile to Old Hillsborough Bay. As testament to the effluent’s purity, bottlenose dolphins frequently can be seen swimming right at the discharge point.