Municipalities Tap into Benefits of EDR Water Treatment
No one wants to drink radium, nitrates or arsenic. However,
if not for some technologically advanced methods of removing these contaminants, we all might be sipping on some very unhealthy water.
The citizens of Washington, Iowa found that out when
problems arose. In 1979, the Iowa Department of Natural Resources notified
Washington that the city was in violation of the radium standard for drinking
water. Even then, radium was recognized as a dangerous carcinogen. Washington
evaluated a number of options for improving the water quality and removing the
radium from the water. Town officials decided on implementing an electrodialysis
reversal (EDR) process. This was a relatively new variation on the
electrodialysis process that had been commercialized by Ionics, Inc., in the
1950s. Thanks to that technology, the city has seen its way clear to having no
water quality problems.
Today, there are many other examples of cities, towns and
municipal organizations that have found EDR demineralization to be an
economical, high performance way to transform nonpotable water into
high-quality, safe drinking water.
EDR is a variation on the electrodialysis process, in that
it uses electrode polarity reversal to automatically clean membrane surfaces.
The electrodialysis process uses a driving force of direct current (DC) power
to transfer ionic species from the feed water through cation (positively
charged ions) and anion (negatively charged ions) transfer membranes to a
concentrate stream, creating a
more dilute stream. EDR works similarly, except that the polarity of the DC
power is reversed two to four times per hour. When the polarity is reversed,
the dilute and concentrate compartments also are reversed. (See Figures 1 and
2.) The alternating exposure of membrane surfaces to the dilute and concentrate streams provides a
self-cleaning capability that enables purification and recovery of up to 94
percent of the feed water.
There currently are a number of alternatives to the EDR
technology for treating and reducing contaminants in drinking water and feed
water. Probably the best known of these processes is reverse osmosis (RO). Both
EDR and reverse osmosis use semipermeable membranes to filter out dissolved
ions from water. However, where RO uses the application of pressure to overtake
osmotic pressure and force water through the membranes, EDR uses voltage
potential to force contaminants through the membranes.
The RO process often has a capital cost advantage over EDR
but can require extensive pretreatment, higher pumping power and more
chemicals. RO also has a lower water recovery rate if the water has positive
An Evolving Technology
Over the last ten to fifteen years, numerous advances in
membrane and system technology have made EDR an especially attractive
technology, both in terms of performance and cost-effectiveness. Improved
membrane technology now allows for one-step machine manufacture of ion exchange
membranes, reducing costs and lowering membrane resistivity. New high
performance spacers (placed between the membranes) allow better transport of
contaminants like nitrates, speeding the process, reducing the number of
membrane stacks required and shrinking costs.
The next generation of EDR systems has made major
improvements in the design. This new design streamlines the process flow with
simpler hydraulics and standardized components, substantially lowering the
capital and operating costs of EDR demineralization. It features the new spacer
technology, as well as a more compact design that is easy to install in an
array of configurations.
The growing popularity among municipalities of the next
generation EDR systems, with their new compact efficient design and
field-tested track record of success, comes as no surprise. In recent years,
completely new EDR installations have taken place around the world for a
variety of applications. At the Ruth Fisher School in Arizona, an EDR system
was installed with the objective of removing inorganic components from
groundwater and reducing nitrates to meet U.S. Environmental Protection Agency
drinking water standards. The nitrate concentration in the feed is more than
100 mg/L, but the EDR system produces water with extremely low total dissolved
solids and nitrate concentrations.
At the Bermuda Water Works, EDR is used to reduce hardness
in the island's existing water supply (600,000 gpd). The brackish water lens
under the island is contaminated from septic tank leach fields, making nitrate
removal essential. The plant removes 86 percent of the nitrates, while
achieving 90 percent water recovery.
In Kazusa Town, Japan, concerns were about nitrate levels as
high as 80 mg/L in the water supply. An EDR system worked to reduce the
nitrates to less than 27 mg/L in order to provide safe, great tasting drinking
water to the city.
After years of proven performance in Washington, Iowa, other
Iowa municipalities have installed EDR, with ever-larger capacities to treat
groundwater for radium, hardness and salinity reduction. Mt. Pleasant, Iowa,
installed a 2.5 mgd EDR system in 1997. Following the old adage that success
breeds success, Fairfield, Iowa, is building an EDR plant to desalt groundwater
that then will be blended in an existing lime softened water system for up to
4.0 mgd of product water.
A new installation near Albuquerque, N.M., is using EDR in a
very deep well water source that has limited flow capacity. This EDR
installation will be removing salinity, arsenic, iron and manganese for the
supply of drinking water. With EDR, 92 percent water recovery is achieved. EDR
was selected for this application because RO was not efficient from a recovery
standpoint with the anticipated level of silica in the raw water supply.
As EDR technologies evolve and improve and efficiencies
increase, one thing is becoming increasingly clear: EDR has a bright future.
EDR systems now are simpler and more reliable, which means that the
demineralization of difficult-to-treat water is easier for municipalities to
handle. In addition, the costs are becoming easier to swallow.