The city of Rowlett, Texas, experienced an unauthorized wastewater ...
The LaGrange, Ind., wastewater treatment facility is a 50-year-old extended air activated sludge plant, designed to treat an average daily flow of 1.8 million gal per day (6,815 cu meters per day) and an average design peak flow of 3.6 million gal per day (13,630 cu meters per day). In a recent review of the plant's performance, all indications were that the operating plan for the plant, which has been managed via public-private partnership by Severn Trent Services since 1997, was resulting in compliant, efficient and cost-effective operations. The staff was operating all processes as intended by the engineer's design, and fulfilling the facility's intended purpose.
But in an era when the global "green" movement is focusing increased attention on conserving resources, mere compliance is not enough. In 2008, under the direction of Seven Trent, the LaGrange plant underwent a process to identify ways it could reduce its carbon footprint.
Implementation of a sewer collection system maintenance program that began in 1999 helped eliminate discharges from numerous combined sewer overflows (CSOs) and sanitary sewer overflows (SSOs). This process is indicative of the successful partnership between Severn Trent and LaGrange. Defining problems and working together to devise and implement solutions is an ongoing, proactive effort. So, when Severn Trent made a formal, companywide commitment to monitor and reduce its carbon footprint in 2008, company personnel implemented a Site Energy Management Plan (SEMP) audit to evaluate and create action plans to improve plant energy efficiency. The ratio of kWh used per million gal treated is the unit of measure used to evaluate a treatment plant's carbon footprint and performance results against any set objectives.
Before Severn Trent recommends any action items resulting from a SEMP, all permit limits and client contractual requirements must be met. Unless all effluent permit and client commitments and obligations are met, no amount of kWh reductions can be justified.
The formal SEMP performs the following actions:
The Severn Trent SEMP Process Model was used to evaluate the current operations of the LaGrange facility. Table 1 details the treatment facility's base model annual average operating characteristics.
While the process model proved the effectiveness of the LaGrange plant's current operation, it also helped Severn Trent personnel identify possible areas of energy reduction, including:
These six strategies, determined by Severn Trent to be the most viable methods of reducing kWh demand at the plant, would represent estimated savings ranging from about $800 per year to more than $13,000 per year.
Evaluating the feasibility of each of the approaches, Severn Trent officials recommended the fourth option. This approach would operate the grit pump on demand, rather than continuously, and with one ultraviolet bank seven months of the year to meet seasonal disinfection requirements. The grit pumps and classifier are currently operated continuously because there is a lack of confidence in the pump priming system and the system freezes in the winter if not run. The issues with the priming system will have to be addressed prior to operating the pump in automatic mode. The estimated annual savings from this approach is 59,220 kWh, a kWh-per-million-gal savings of 10% compared to current performance.
"The results of the SEMP audit show that plant management and staff are putting forth a strong effort to optimize operations,” said Clint Houseworth, process specialist for Severn Trent Services' Technical Services Group. “Severn Trent is committed to continuously looking for opportunities to save energy through creative thinking that will be incorporated into long range comprehensive planning goals. While the LaGrange plant is currently operating efficiently and effectively, creating a SEMP to guide our operating decisions will ensure even greater process and operational efficiencies in the years to come through reduced energy usage."